Cable fault tester integrated industrial embedded computer platform, Network Communications Service and USB communication system to improve the utilization of the device. Specially, the device has loaded a system for underground buried cable data save and meet the national standard of 《DL/T849.1～ DL/T849.3-2004》.Cable fault tester is used for cable fault location, cable line and depth test and daily maintenance of cable data. It can also be used for signal cable fault location for railway station and airport.
◆ We are the first company in China who use industrial embedded computer platform system into cable fault locator. Lithium-power supply affords the convenience of field tests.
◆ We are the first company in China who use 12.1 inch touch-screen and windows XP system.
◆ The Cable fault tester adopt USB communication interface. The host can select 5 sampling frequency automatically between 6.25 MHz to 100MHz for the cable of different length.
◆ The Cable fault tester can search the fault point and display the distance automatically, the movement of double cursor can be accurate to 0.15m. The waveform can be compressing or expanding freely. At the same time the system will display two waveforms randomly which is close to standard waveform for your reference.
◆ The Cable fault tester saves total 40G waveforms and on-site wiring diagrams for your reference.
◆ We developed smart modular sampler to replace the on-site wiring, the sampling is totally separated with high-voltage to ensure the safety of the operator.
We developed HP-G35 high frequency high voltage power supply (8.9Kg) to replace the testing transformer and operation box (65Kg).
1.It can be used for test cable fault for different voltage levels, different sections and
different medium, including open circuit, short circuit, low resistance, high resistance
leakage, high resistance failure flashover.
2.It can be used for testing signal cable fault for railway station, airport.
3.It can be used for testing wave propagation speed of the cable which length is known.
4.It can be used for testing the cable route and depth.
1.Display mode: 12.1 inch LCD (Windows XP)
2.Test pulse range: about 400VP-P
3.Test methods: Low-voltage pulse method, impulse flash-over circuit method, flashover
4.Test distance: no less than 40km
5.The shortest testing distance (blind zone):5-10m
6.Location error: ±0.5m
7.Testing error: less than ±1%
8.Sampling frequency: 120MHz、90MHz、60MHz、30MHz、15MHz
9.Power: AC 220V±10% DC 12V（7AH）
10.Maximum power endurance: 3 hours
11.Signal frequency: 15KHz sine wave
12.Output power: Pomax≥100W
13.Output impedence: Zo=Zc
14.Vibration mode: incontinuous
15.Host Weight: 9.8Kg
16.Ambient temperature: －10℃～＋40℃
17.Overall dimension: 180mm×300mm×400mm
18.Relative humidity: RH≤85%（25℃）